Boiler water treatment equipment, boiler water treatment water softener, boiler water softening equipment, resin water softening equipment
Water softener can be divided into time control type, flow control type, continuous water supply system type, and there are various combinations of single valve single tank, single valve double tank, double valve double tank parallel, large multi-valve multi-tank series, etc. To meet users' different water needs. The flow type is a fully automatic regeneration of the set flow control. The flow size can be set according to the different resin loading and water quality. The time type is based on the resin filling amount and water quality combined with the hourly specific demand to convert the time, and the fully automatic regeneration is controlled by the set time.
1. Imported control valve: The material of the valve body is high-strength, lightweight, corrosion-resistant engineering plastic, lead-free brass.
2. Anti-corrosion tank: The tank is made of glass fiber reinforced plastic (optionally carbon steel or stainless steel lined plastic tank). The tank is corrosion-resistant, pressure-resistant, and has a long service life.
3. Uniform water distribution system: Adopting jet water distribution, the effective exchange capacity of the resin can be fully exerted, and the salt control is accurate without the need for a salt pump.
4. Imported high-performance resin: Strongly acidic cation exchange resin is selected, with low damage rate, uniform particle size, and improved ion exchange rate.
The working principle of the automatic softening water treatment equipment The hydraulic control valve uses the kinetic energy of the water flow to drive two sets of turbines to drive the two sets of gears to push the water meter and control panel to rotate. The water meter plate accumulates the flow, and the control plate introduces the raw water pressure signal into a group of valve chambers through a group of channels, and opens or closes the pressure channels according to a set rule while rotating, thereby realizing automatic switching of a group of valves integrated into one .
The water softener is composed of two resin tanks (main tank and auxiliary tank) hydraulic control valve and salt tank. The control valve controls the water path to switch between the main tank and the auxiliary tank, ensuring that one tank is always in working state and the other The tank is in the state of regeneration or standby. The regenerating salt liquid is sucked by the negative pressure of the venturi ejector installed in the valve. The regeneration and cleaning water is the softened effluent of the other tank. For different raw water hardness, water dials with different numbers are used to achieve corresponding working and regeneration cycles.